CONTROL PANELS EN FOR MOTOR-POMP
Electric control panels for fire-fighting motor pumps according to European standard UNI EN 12845
Low voltage inputs and control circuits;
2 normally closed inputs for starting pressure switches;
2 Inputs from external batteries for starter motor and auxiliary circuits supply;
Input for control from priming tank;
Input for pressure switch/pump switched off;
AUT-EMERGENZA key selector switch;
Manual start and stop motor pump buttons;
Button to restore anomalies;
Manual start test button (active in case of automatic start failure);
Button test led control unit;
Manual Emergency start buttons protected by "Safe crash";
Backlit LCD display for display n. 2 voltmeter batteries, n. 2 amperometers batteries, rev counter, total and partial counter, fuel level indicator, water thermometer, oil thermometer, oil pressure gauge, batteries and historical events;
Led of signaling;
Possibility of operation according to UNI10779;
Display with 5 languages: Italian, English, French, Spanish, German;
Adjustable delay and alarm functions;
Alarm outputs for: automatic mode excluded, control panel failure, motor pump in operation, failure to start;
2 charger 12vdc 3A (24vdc 3A for 24V version);
Auxiliary protection and motor with fuses;
General disconnector block door;
Metal casing, IP55;
Ambient temperature: -5/+40 ;
Relative humidity 50% at 40 ºC (not condensed).
DIESEL-EN PLUS 500
DIESEL-EN PLUS 800
Power-supply 1 ~ 50/60Hz 230V±10%;
Benefits control panels EN for motor pump
Compared to the previous UNI9490 standard, many more conditions have been added to be monitored and transmitted to a manned room or to a responsible person who can intervene immediately.
The rule also clarifies that the fire protection system must be certified in its complexity.
The pumping system and/or switchboards may be declared to conform to the standard by means of a manufacturer’s self-certification.
European Standard EN12845
The European standard UNI EN 12845 deals with fixed fire-fighting installations and the design, installation and maintenance of automatic sprinkler systems.
Mainly EN 12845 deals with giving rules and indications on the sizing of fire-fighting systems and the type of pumps, prescribing some general requirements and others specific to particular pumps.
Each pump must be installed with its own control panel in the same room, with the obvious exception of submersible pumps.